Synchronization panels are mainly designed and used to meet power system requirements. These panels function both manually and with an automatic synchronizing function for one or more generators or breakers.
They are widely used in synchronizing generators and offering multiplex solutions.
Our high quality range of synchronizing panels is available with capacities that reaches 10000 A, and are fabricated by our engineers using premium quality electrical components including copper bus bar, insulations, wires/cable, PVC channels, transformers, meters and switches.
Our Synchronizing panel will operate on an automatic mains failure system, so that when the main supply is interrupted on one or all phases (after an adjustable delay period) the generator sets will start-up together. After an initial warm-up period (adjustable) the generators will synchronize with each other by means of motorized circuit breakers or contactors onto a common busbar. Next, the motorized change-over switch will be closed and the load will be connected to the main distribution box.
The load share units continuously monitor the load and during low demand periods one or two generators will be shut down to save on fuel consumption. As demand rises again the second generator and third generator will be restarted, synchronized and reconnected to the load. When the AMF control unit detects that the main supply has been restored an adjustable observation period is activated before the main supply is reconnected. A cool down period will then follow, after which the generator sets will be shut down.
Key features of General Control & Synchronization Panel
OUR MANUFACTURING CAPABILITIES ALLOW US TO BUILD ANY CONFIGURATIONS AND CUSTOMISED TRANSFER & CHANGE OVER SWITCHES. CONTACT US FOR FREE DESIGN/CONSULTATION AND QUOTATION.
24 HOUR PROTECTION AGAINST POWER FAILURES
Automatic transfer switches are used to automatically change over from the main electrical supply to stand-by generators or generate on failure of the main supply.
When the main supply is restored, the system automatically changes back and stops the generator. The stand-by generator will eventually be shut down after a short cooling down period.
These panels are provided with mechanically or electrically interlocked pole contactors or MCCB.
AUTOMATIC & MANUAL TRANSFER SWITCHES
AUSSIE POWER SOLUTIONS
Belong to NT - Belong to YOU
ELECTRICAL MANUFACTURING AND ENGINEERING SPECIALIST